Heating and Air Conditioning Homeland, CA
for Homeland, CA
AC Service Fast and Complete
Jackie - Homeland, CA
Cooling maintenance in homeland on package unit replaced filter and cleaned condenser coils. Inspected compressor and motor operations and test ran system from thermostat. System is cooling and tested vent temperature and return temperatures.
Performing an air conditioning service call on a Rheem condenser.
Performing an air conditioning service in regards to a thermostat that is not operating.
Service call no heat in homeland and found faulty thermostat. Replaced thermostat and system is active.
Performing a no heat service call on an Intertherm downflow furnace.
Heating maintenance on Coleman furnace inspecting blower motor and capacitor ratings as well as circuit board and gas valve operation.
Heating maintenance inspected capacitor from blower motor and thermostat settings, electrical inspection and voltage readings.
Heating maintenance for customer in homeland inspected and gas furnace unit and inspecting blower motor